National Service Hotline:
Zibo Taylor Heat Exchange Equipment Co., Ltd.
Address: Boshan District, Zibo City, Shandong Province
Contact: Gao Qing
Mobile phone: 13409069825
When we use a plate heat exchanger, we sometimes find some leakage. When we find a plate heat exchanger, we must first identify the cause and then find a solution. The plate heat exchanger manufacturer recommends that you perform the following methods:
1. In the no-pressure state, re-clamp the equipment according to the clamping size provided by the manufacturer. The dimensions should be uniform and the deviation of the pressing dimensions should not be greater than ¡À 0.2N (mm) (N. is the total number of plates). The parallelism between the tight plates should be kept within 2mm.
2. Make a mark on the leak, and then disassemble the heat exchanger one by one to solve it, reassemble or replace the gaskets and plates.
3. Disassemble the open heat exchanger and repair or replace the deformed part of the plate. When no spare parts are available, the deformed parts can be temporarily removed and reassembled.
I hope the above introduction of the plate heat exchanger can bring some help to everyone. Thank you for reading. If you have any needs, please contact us.